||Weak-Acid Ion Exchange for Removing Barium, Radium, and Hardness.
Snyder, D. W. ;
Snoeyink, V. L. ;
Pfeffer, J. L. ;
||Illinois Univ., Urbana.;Environmental Protection Agency, Cincinnati, OH. Water Engineering Research Lab.
Ground water ;
Ion exchange resins ;
Ion exchanging ;
Water pollution control ;
||Most EPA libraries have a fiche copy filed under the call number shown. Check with individual libraries about paper copy.
||Weak-acid resin in the hydrogen form was found to effectively remove barium, radium, and hardness, without increasing the sodium content of the product water. The maximum capacity of the weak-acid resin was about 2.3 times that of strong-acid resin, and much less spent regenerant per unit volume of water treated was produced from a weak-acid column than from a strong-acid column. There are, however, some disadvantages to weak-acid ion exchange: swelling of the resin during exhaustion; the need to use acid-resistant materials; the inability to remove noncarbonate hardness; the necessity of stripping carbon dioxide from the product water and adjusting the pH; and the probable higher cost.
||Pub. in Jnl. of American Water Works Association, v78 n9 p98-104 Sep 86. Sponsored by Environmental Protection Agency, Cincinnati, OH. Water Engineering Research Lab.
|NTIS Title Notes
||Reprint: Weak-Acid Ion Exchange for Removing Barium, Radium, and Hardness.
|PUB Date Free Form
||PC A02/MF A01