Record Display for the EPA National Library Catalog
RECORD NUMBER: 18 OF 271
|OLS Field Name||OLS Field Data|
|Main Title||Applying fabric filtration to refuse-fired boilers : a pilot-scale investigation /|
|Author||McKenna, J. D. ; Mycock, J. C. ; Miller, R. L. ; Brandt., K. D. ;|
|CORP Author||Nashville Thermal Transfer Corp., Tenn.;Industrial Environmental Research Lab., Research Triangle Park, N.C.|
|Publisher||Environmental Protection Agency, Office of Research and Development, Industrial Environmental Research Laboratory ; For sale by the National Technical Information Service,|
|Report Number||EPA-600/7-78-078; EPA-R-804223|
|Subjects||Filter cloth. ; Dust control. ; Refuse as fuel. ; Dust control. ; Filter cloth. ; Refuse as fuel.|
|Additional Subjects||Air pollution control ; Boilers ; Pilot plants ; Dust collectors ; Feasibility ; Industrial wastes ; Combustion products ; Glass fibers ; Laminates ; Particles ; Cost analysis ; Operating costs ; Design criteria ; Performance evaluation ; Fluorine organic compounds ; Fabric filters ; Refuse derived fuels ; Ethylene/tetrafluoro|
|Collation||xi, 123 p. : ill. ; 28 cm.|
The report gives results of a pilot-scale investigation to determine the techno-economic feasibility of applying fabric filter dust collectors to solid refuse fired boilers. The pilot facility, installed on a slipstream of a 135,000 lb/hr boiler, was sized to handle 9000 acfm at an apparent filtering velocity of 6 fpm. Filter media evaluated included a woven glass, a felted glass, and a PTFE laminate on a woven backing. The three filter media had overall efficiencies greater than 99.8%, at apparent filtering velocities of 6 fpm or less, with an inlet loading of 0.5 gr/dscf. For the brief exposures during performance testing, none of the bag materials showed any wear problems. Installed costs for a woven glass fabric filter (the least expensive material tested) capable of handling 140,000 acfm were $317,000, $422,000 and $817,000 ($2.26, $3.01, and $5.83/acfm, respectively) at corresponding air-to-cloth ratios of 8.9, 5.8, and 2.9. Installed, operating, and annualized costs for other filter media, as well as costs for electrostatic precipitation and wet scrubbing, are also presented.
Prepared by Nashville Thermal Transfer Corp. under Grant no. R804223, program element no. EHE624. Issued May 1978.